Did you know that you can group control all type of indoor units throughout the Fujitsu single and multi split range. Although a relatively simple feature it is not possible with most of the competition and the ability to group control wall mounts and multi systems is particularly unique.
Below we have highlighted examples and the procedure for these unique applications.
The procedure applies to all the models as follows:
* communication kit required for each indoor
Examples of Multi Split Group Control
Maximum wiring length of remote controller cable is 300m and should be increased when greater than 100m as per the table below.
|Control Cable Length
|100m or less
The RC Group Address is set via the remote controller (wireless or wired).
|Remote Controller Address
|00 – 15 (default value 00)
Each indoor requires an address value between 00-15 as detailed in Example 1
Please note is not possible to group control across multi systems as highlighted below
For further information download the PDF or contact your local branch on the numbers below.